Only trained and qualified professionals can carry out the installation, please follow the instructions in "safety precautions". During the installation process, you must ensure that the converter's power supply has been disconnected. If the inverter have electricity, so after a POWER outage, and short waiting time is not on the inverter marked time, and make sure the POWER light is extinguished, it is recommended that the user uses multimeter to ensure the DC bus voltage is below 36V.
Frequency setting range of inverter can reach 0-400Hz. For applications with high output frequency requirements, we can supply CHV150 products with an output frequency of up to 3000HZ.
Running environment temperature is between - 10℃ ~ + 40℃, derate by 3% for each additional 1℃, the max operation temp should not exceed 50℃. Relative humidity of air is < 90% without condensation. When the installation site of the inverter is below 1000m, it can be operated at its rated power. When the elevation exceeds 1000m, it will be used at a proportional decrease of 1% of the 100m. The maximum amplitude is no more than 5.8m/S2 (0.6 g) and the inverter should be away from the source of electromagnetic radiation. The installation site should be free from oil mist, corrosive flammable gas, no radioactive material, metal dust, dust, oil, water and other foreign objects.
CHF100A 380V CHF series 15KW (including) GD series 30KW (including)
GD35 GD300 GD300 GD800 IPE200 CHA100\CHV100A\CHV190
When the motor starts, it will flow through the starting current corresponding to capacity, the transformer on motor stator side will generate voltage drop, the impact of voltage reduction is large when motor capacity is large. The inverter connected to the same transformer will report undervoltage or transient stop and cause protection function to act, thus operation is stopped.